Shenyang SIWO Electrical Equipment Co., Ltd.
Add:No.22, Puyu Road, Dadong District, Shenyang City, Liaoning Province, China
Contact us:Gu Yu
1) clean the porcelain surface dust, check whether the surface of porcelain enamel, damaged, there is no sign of cracking and flashover, iron, porcelain insulators binding site is solid. If serious damage, should be replaced;
2) use gasoline to clean the oil on the blade, contacts or contact, check the contact surfaces are clean, there are no mechanical damage, oxidative and signs of overheating and distortion, deformation and other phenomena;
3) check the accessories are complete on the contact point or blade, there is no damage;
4) check the connection isolation switches and Busbar, circuit breaker wire is solid, with or without overheating;
5) check the soft parts to be joined, such as having an impairment, broken;
6) review and cleaning devices and transmission parts, and adding the right amount of grease;
7) check the transmission part of the distance from live parts to meet requirements; Locator and brakes are solid, action is correct;
8) check the base of the disconnecting switch is good, grounding is reliable.
- Isolating Switches
- Main Disconnecting Switch
- Low-voltage Isolate Switch
- Low-voltage Circuit Breaker
- Choice Of Disconnecting Switch
- Operating Range
- Order Of Operations
- Frequently Asked Questions
- 2016 Ho Chi Minh City, Vietnam Inte...
- 2016 India Bangalore International ...
- 2016 Made In China Qatar Exhibition
- 2017 Dubai International Electricit...
- 2017 Russia Moscow International Po...
- Circuit Breakers Can Be Used To Dis...
- Circuit Breaker Is To Control The E...
- Circuit Breaker Working Principle
- Vacuum Circuit Breaker In The Annua...